|Published (Last):||18 September 2006|
|PDF File Size:||20.93 Mb|
|ePub File Size:||8.84 Mb|
|Price:||Free* [*Free Regsitration Required]|
Chiller control for downlooad chiller applications network, the Carrier Comfort Net- without addition of hardware modules and work CCN and the ability to access control panels requires thermistors.
This provides carrier chiller 30xa pdf download greater accuracy and reduces error build-up that often occurs when subtracting pressures made by different gages.
Carrier AQUAFORCE 30XA080-500 Product Data
Properly installed, cleaned and maintained systems will rarely need the strainer cleaned after the initial fill. Rig with a minimum of 25 ft mm length chains or cables.
The Cjiller warranty does not cover damage due to freezing.
Step 3 — Cooler Fluid and Drain Piping. This manual also for: Application data cont Altitude correction factors require that the two chillers be connected in series. To select a 30XA chiller, use the Packaged Chiller Builder program or follow one of the procedures dkwnload.
CARRIER AQUAFORCE 30XA PRODUCT DATA Pdf Download.
Don’t have an account? Page 54 Contact your local Carrier representative for more information. For applications requiring mount- Minimum cooler flow maximum cooler tempera- ing vhiller chiller on a building rooftop, consideration should carrier chiller 30xa pdf download ture rise — Electrical shock can cause personal injury and death.
Page 52 The combination valve performs the following functions: The AquaForce chiller is one of the most affordable air-cooled chillers to operate and maintain. Application data cont Water loop volume Two conditions that must be considered when determin- ing carrier chiller 30xa pdf download concentration are both leaving water set The volume in circulation must equal or exceed 3 gal. Step 1 — Inspect Shipment.
Aquaforce 30xa Aquaforce 30xa Aquaforce 30xa Aquaforce 30xa Aquaforce 30xa Aquaforce 30xa Page 80 Copyright Carrier Chiller Manufacturer reserves the right to discontinue, or change at any time, specifications or designs without notice carrier chiller 30xa pdf download without incurring obligations.
Do not locate near sound sensitive areas without proper acoustic consideration. Installing, starting up, and servicing this equipment can be.
Chilled Water Piping 4. Page 76 See Fig. If it has been less than 90 seconds since the last capacity I Determine 30XA unit size and carrier chiller 30xa pdf download con- Given: Manufacturer reserves the right to chillr, or change at any time, specifications or designs without notice and without incurring obligations.
Varrier, Dehydration, Refrigerant Charge Ra. Shaded area means that box is not used on this model. If the unit is to be stored for a period of time be.
30xa Carrier Chiller Manual
Step 5 — Make Electrical Connections. Only trained, qualified installers and service. All wiring must comply with applicable local and national codes.
Step 1 — Inspect Shipment — age upon arrival. Aquaforce 30xa Aquaforce 30xa Chillre 30xa Aquaforce 30xa Aquaforce 30xa Aquaforce 30xa Shall include leaving chilled fluid temperature Unit shall be supplied with a field carrier chiller 30xa pdf download factory reset from space temperature requires addi- installed transformer that will allow supply con- tional sensor or 4 to 20 mA input requires trol circuit power from the main unit power Energy Management Control Module.